By now, the domestic hot water (DHW) supply system has been organized in compliance with the Latvian building normative LBN „Buildings’ Internal. These Regulations shall affirm the Latvian Construction Standard LBN with the Latvian Construction Standard LBN “Internal Water Main and . Construction normative LBN “External network for water Construction normative LBN “Internal water and sewage water.
|Published (Last):||19 July 2011|
|PDF File Size:||17.6 Mb|
|ePub File Size:||16.94 Mb|
|Price:||Free* [*Free Regsitration Required]|
In rooms with exits to a dead-end corridor or hall.
EUR-Lex Access to European Union law
If pressure in the external water supply cannot ensure the operation of fire-extinguishing installations, pumps shall be installed for the starting of which the following shall be used:.
Number of people on emergency evacuation routes in halls for public events. This circumstance changes considerably the input kbn for calculation of DHS elements, making it possible to work out appropriate measures in order to improve the DHS efficiency through step-by-step replacement of the elements with high energy loss.
The internal network of fire taps shall be a loop with two supply pipes from the external network, as well 22198 with an isolation device for the sprinkler and drencher system.
Influence of Changes in Hot Water Consumption on the DHS Development
DHS development ; environment management methods ; hot water consumption. Number of people per 1 m of the width of the lgn route door if the volume of the hall is thousand m 3. Household and drinking water supply pumps shall be installed on a vibration-insulating base and separated from the supply pipes and the internal network with flexible spacers.
Isolating shut-off dampers in the network shall be so installed that there are not more than two branches in the sector to be shut off. Research Institute of the University of Central Florida. 212-98
EUR-Lex – LLVA_ – EN – EUR-Lex
The summary calculated water consumption shall be the largest of the following two internal fire-fighting system usages if:. In the work, experimental results are presented that have been obtained through monitoring the hot water consumption. Buildings at cultural and entertainment institutions shall have the following fire-fighting equipment:. Dampers shall be installed for the main branch pipes having more than two fire taps.
In stage work galleries it is permissible to connect fire taps to the upright tubes of the stage sprinkler system. Issue 6-II Issue 6-I: The primary emphasis was given to the hot water consumption, with its noticeable daily fluctuations as well as changes caused by those in the inhabitants’ way of life.
Strategy of Energy Economy. De Gruyter – Sciendo. The Journals of Communal Services. The Cabinet of Ministers of the Republic of Latvia. Pressure in the fire taps located on the boards of the stage shall ensure a compact water spout, which exceeds the distance from the boards to the coverings of the flies by two meters. Issue 3 First Online: In rooms located between staircases or exits to the outside. User Account Sign in to save searches and organize your favorite content.
If the capacity of the external water supply is not sufficient for the supply of the calculated amount of water for the elimination of fire or if the supply pipes are connected to the closed networksunderground reservoirs shall be created the volume of which shall ensure:. Fire taps shall be installed:.
Drenchers for the stage portal and scenery safe shall be divided into two separate sections. The methodology, which is in good agreement with the ideology of advanced management of DHS development, employs the ISO series of standards widely applied in the sphere of kbn management. Minister for Environmental Protection. Drencher devices shall be installed beneath the stage and proscenium fliesbeneath the lower work gallery level 221-98 the joints thereof, beneath the lower footpaths, as well as in the scenery safe and all stage passages including portal passages, pockets and proscenium and in the stage engine room.
A drencher device may have the following control function:. Sign in to annotate. Additional energy saving in a building with improved insulation. Budjko 1 and V. In order to be able to connect hoses of mobile fire-fighting pumps, two pipes shall be provided from the penstock between the pumps at the isolation device of the sprinkler and drencher devices the diameter of which shall be 80 mm and which shall be fitted with check valves and the standard connections of fire-fighting hoses.
Table 8 Distance to the emergency exit Fire safety level of the building. The goal of the authors was to clarify how the district heating system DHS development is affected by the heat consumption. The results evidence that this consumption and its usage indices correspond to the level achieved by Western in particular, North-European countries.
Fire taps shall be so installed that in the case of fire any point in the room could be extinguished with two spouts. If the area of the boards of the stage is up to m 2three fire taps shall be installedif the area is larger — four fire taps shall be installed and they may be open, without lockers.